The Motion Sensor Switch adopts good sensitivity detector, integrated circuit. It gathers automatism, convenience, safety, saving-energy and practicality functions. The wide detection field is consisting of detectors. It works by receiving human motion infrared rays.When one enters the detection field, it can start the load at once and identify automatically day and night.Its installation is very convenient and its using is very wide. It has functions of power indication and the detection indication.
Power Source: 110 -220V/AC
Detection Range: 360°
Power Frequency: 50Hz
Working Temperature: -20°C~+40°C
Ambient Light: 3-2000LUX (adjustable)
Working Humidity: <93%RH
Time-Delay: min: 10sec±3sec Max: 7min±2min
Installation Height: 2.2-4m
Power Consumption: 0.45W (work) 0.1W (static)
Rated Load: 1200W (incandescent lamp) 300W (energy-saving lamp)
Detection Motion Speed: 0.6 ~1.5m/s
Detection Distance: 6m max (24°C)
1.Can identify day and night: The consumer can adjust work ambient light. It can work in the daytime and at night when it is adjusted on the "sun" position (max). It can work in the ambient light less than 3LUX when it is adjusted on the "moon" position (min). As for the adjustment pattern, please refer to the testing pattern.
2.Time-Delay is added continually: When it receives the second induction signals after the first induction, it will compute time once more on the basic of the first time-delay rest.
3.Time-Delay is adjustable. It can be set according to the consumer's desire. The minimum time is 10sec±3sec. The maximum is 7min±2min.
1.Switch off the power.
2.Turn clockwise the bottom-stand and take off it. The power wire cross the hole in the middle of bottom-stand.
3.The bottom-stand is fixed on the selected position with inflated screw.
4.Connect the power and the load into the connection-wire column of the sensor according to connection-wire diagram.
5.The sensor aimed at the mouth of bottom-stand and turned anti-clockwise.
1.Turn the TIME knob to minimum (-) position with anti-clockwise. Turn the LUX knob to SUN position with anti-clockwise.
2.Switch on the power; the controlled load and indication lamp both are not working. Preheat 30 sec later, the load and indication lamp should be turned on synchronization. In the absence of no inductor signals, the load should be stopped working within 5-30sec, the indicator lamp is turned off.
3.After the first sense is finished, and it will sense again after 5~10sec. The load should work. When there is no inductor signals in the indicator lamp, the load should be stopped working within 5-15sec.
4T.urn LUX knob clockwise on the minimum (MOON position). If it is adjusted in the less than 3LUX, the inductor load should not work after load stop working. If you cover the detection window with the opaque objects (towel etc), the load work .under no induction signal condition, the load should stop working within 5-15sec.